Ground Fault Circuit Interrupter Wiring Diagrams
–Check local regulations for restrictions and permit requirements before beginning electrical work–
This page contains wiring diagrams for ground fault circuit interrupter (gfci) receptacles. Included are diagrams for multiple gfci's, a protected standard duplex receptacle, and a protected light fixture. Wiring for a switch and gfci receptacle in the same box is also shown to protect the switch and light or to protect other receptacles in the circuit. To wire a gfci circuit breaker see this link and wire a gfci switch combo at this link.
GFCI Outlet and Light Switch
This diagram illustrates wiring a GFCI receptacle and light switch in the same outlet box, a common arrangement in a bathroom with limited space. The hot source is spliced to the LINE terminal on the receptacle and to the bottom terminal on the light switch. The neutral and ground wires are spliced together and run to each device in the circuit.
Multiple GFCI's with Protected Duplex Receptacle
This gfci wiring provides protection to a duplex receptacle. By connecting the load terminals on the last gfci, the receptacle is protected and can be used just as if it were one of the gfci receptacles. One ground fault circuit interrupter at the beginning of the circuit can be used in the same way to protect multiple, subsequent receptacles as illustrated in the diagram below.
Multiple GFCI's and a Duplex Receptacle
This diagram illustrates the wiring for multiple ground fault circuit interrupter receptacles with an unprotected duplex receptacle at the end of the circuit. The load terminals on the gfci are not used and the last receptacle is wired directly to the circuit source.
GFCI with Protected Light
This diagram illustrates the wiring for a circuit with gfci receptacles followed by a light and switch. By connecting the switch to the load terminals on the gfci, the light is protected against ground faults as well.
GFCI with Unprotected Light
This diagram illustrates the wiring for a circuit with gfci receptacles followed by an unprotected light and switch. The light switch is connected directly to the source and the load terminals on the gfci are not used.